چراغ های هشدار ضد انفجار NM
Marking to ATEX 94/9/EC Directive:
II 2 G Ex d IIC T4 or T3 / II 2 D Ex tD A21 IP65 T130ºC or T195ºC
Zone: 1, 2, 21, 22 , Gas Group IIC
Compliance with: IEC 60079-0:2004, IEC 60079-1:2003,
IEC 61241-0:2004, IEC 61241-1:2004
EC Type Examination Certificate: ISSeP07 ATEX 022
Applicarion: Single or double warning lights normally installed on tower or high buildings for
Enclosure: Copper free aluminium alloy suitable for petroleum and marine locations.
Glass: Borosilicate tempered glass resistant to impact and sudden heat changes.
Fresnel globe: Polycarbonate normally red but also available in yellow, green or blue.
Lamp: Long life low power consumption, LED, incandescent, …
Control Box: Optional electronic control box for ON-OFF flashing. Also available with adjustable
photocell for operation at darkness.
IP rating: IP65 to IEC 529 / EN 60529. IP66 by application of an approved
Installation: Wired to junction box with optional mounting attachments for
any type of installation.
Wire guard: Stainless steel wire guard suoolied with all lighting fixtures, as standard.
Cable entries: ISO 965.1 metric as standard. NPT or other threads supplied on request.
Earthing: Standard M6 internal and external earth screws.
Finish: Electrostatic powder coated or two pack epoxy paint.
Specify “Single” or “Double” warning light.
Installation attachments, for “Direct” or “Conduit” mounting.
Fresnel globe color if different from red.
Control box with adjustable ON-OFF flashing. With or without photocell.
Voltage transformer: 110 V AC, 24 V AC or DC … .
NMWL.. Installation Types and Accessories
Each type is supplied with all accessories shown above.
The assemble is completely wired up to the control box.